Where is the focus of the self cleaning filter installation?
Self cleaning filters should be installed for easy access. Install shut-off valves before and after, and install bypass pipes. Sufficient maintenance space should be left on both sides of the self cleaning filter. The direction of the filter cartridge should be kept close to the length of the cylinder to replace the filter.
The specifications of the self cleaning filter should match the pipe or flow. When a single filter cannot meet the system flow requirements, two or more can be connected in parallel to meet the system filtration requirements. When adopting any type of installation, care should be taken to make the outlet direction of the automatic drain valve horizontal or downward to ensure a more thorough discharge.
When installing and using, pay attention to the protection of the control box, sensor and transmission parts to prevent damage. Connect the pipe according to the direction of the arrow on the self cleaning filter body so that the water flow direction is consistent with the arrow body on the body. Install the water equipment that needs protection before it is as close as possible to the water equipment.
The automatic drain valve connection method is divided into flange and thread, and the drain pipe should not be too long, preferably not more than 10 meters. When the self cleaning filter is installed outdoors, please pay attention to waterproof and rainproof, in order to help extend the life of the device and improve its use.